358 BEKA SCHRÉDER Product Catalogue
Corrosion-proof GRP body and lid
Easy access for maintenance
Various reflector options
Ingress protection - IP 65
APPLICATIONS Industry | Mining | Public buildings | Corrosive
CONSTRUCTION DETAILS The luminaire consists of an injection-moulded, flame
retardant GRP body and lid with clip-in lamp holders for
both single and double lamp versions. It is designed to
operate fluorescent T8 and T5 lamps up to 2*80W.
SABS MARKS The luminaire bears the SANS 60598-2-1 safety mark.
INGRESS PROTECTION The luminaire has a degree of protection that complies
with SANS 60598-2-1:
Lamp compartment: IP 65
Body: IP 65
BODY The body is manufactured from injection-moulded,
flame-retardant glass fibre reinforced polyester and is
provided with a knockout facility at each end, making it
suitable for surface wiring.
Four plastic bolts are clipped into the body onto which
the lid screws tight.
INDUSTRIAL FLUORESCENT LUMINAIRE
A silicon sponge gasket is fitted into a groove
arrangement on the body.
For mounting, two holes are provided in the base of
LID The lid is manufactured from the same material as
the body and is designed in such a way that it can
accommodate the applicable control gear for the
various lamp wattages.
The lid is screwed down onto the body by four GRP
wingnut shaped fasteners that screw into the stainless
steel bolts provided in the body.
External access to the starter is achieved by removing
a screw cap cover.
Two rectangular shaped holes are provided on the lid
to accommodate the clip-in lamp holders, which are
provided with gaskets to ensure the integrity of the
CONTROL GEAR COMPARTMENT The ballast is mounted directly onto bosses provided
on the lid, and the capacitor is held in position by a
suitable slotted clamp.
It is suitable for operation with the specified rating of
the lamp on a 230V +3%/-10% 50Hz single phase
All control gear components are removable and bear
the relevant SABS mark.
Mains connections are by means of a suitable screw
terminal block with a wire clamping contact.
The luminaire is power factor corrected to a minimum